Buy all Datakom genset controllers, energy meters, panel meters, synchronization controllers, auto mains failures (AMF), auto transfer switches (ATS), generator battery chargers, etc. in Pakistan. You can buy DKG155 Manual Start Gennset controller of Datakom online anywhere from Pakistan or by visiting Electronic Power House (EPH) and Tetralink Technologies (TLT) in Lahore who are the authorized distributor of Datakom in Pakistan. All original geneset controllers & AVRs from all over the world are available at very reasonable and best prices in Pakistan.
- Microprocessor controlled
- Manual fuel control and start
- Automatic shutdown on fault condition
- Survives cranking dropouts
- Digital display of generator frequency
- High engine temperature protection
- Low oil pressure protection
- Overspeed-under speed protection
- Spare fault input
- Alarm output
- Two-part connectors for easy replacement
- Standard panel dimensions (72x72mm)
- Low cost
- Low failure rate
The DATAKOM model DKG-155 is a microprocessor-controlled unit designed to start and stop the genset manually using the key switch on the front panel.
In the OFF position, the DC supply is removed from the module, thus zero power consumption is achieved. The unit powers up when the RUN position on the front panel is selected. This will also energize the fuel solenoid relay. The engine is started using the next spring-loaded position marked START. Once the engine has started, the switch should be released. To shut down the engine, select the OFF position on the switch. When the engine is running, the unit monitors fault conditions and shuts-down the engine automatically in the occurrence of an alarm. The alarms are identified by a group of LEDs displaying only the first occurring one.
The alarm checking is only enabled after the protection hold-off timer is expired. This timer is set to 45 seconds when the unit is powered up, it resets to 10 seconds if the engine gets running.
The occurrence of below fault conditions will cause the engine to be stopped immediately:
-High engine temperature,
-Low oil pressure,
If a fault condition occurs, the FUEL solenoid will be de-energized and the led associated with this condition will turn on. Only the first occurring fault will be indicated. To reset the fault condition, turn the switch to the OFF position for a few seconds. The Charge Fail condition is treated as a warning and does not cause the engine to stop. The input monitors the D+ terminal of the charge alternator. The limits for the correct generator frequency are 30 to 57 Hz for 50Hz operation and, 30 to 68Hz for 60Hz operation. The unit uses high current two-part connectors for easy replacement.