EPH-106 AMF Genset Controller
Buy all EPH Genset controllers, energy meters, panel meters, synchronization controllers, auto mains failures (AMF), auto transfer switches (ATS), generator battery chargers, etc. in Pakistan. You can buy EPH-106 AMF Auto Mains Failure Card For Generator of EPH online anywhere from Pakistan or by visiting Electronic Power House (EPH) and Tetralink Technologies (TLT) in Lahore. We are the manufacturer of EPH controllers in Pakistan. We have all original EPH Genset controllers and AVRs ready in stock. All international & local brands of generator controllers are also available at very reasonable and best prices in Pakistan.
Key Features of EPH-106
- Microprocessor controlled
- No need to put any extra timer
- Automatic fuel control and start
- Automatic shutdown on fault condition
- LEDs for fault monitoring
- Screw type connectors for easy connections
- Survive cranking drop-outs
- Small size
- Manual fuel control and start
- Low cost
- Adjustable self-time
- Low failure rate
Description of EPH-106
The model EPH-106 is an advanced version of our very popular model EPH-106 with some extra features like an Auto/Manual switch, additional relay for Mains load, and fewer wiring connections. This is a microprocessor-based control unit that is specially designed for Genset. It can be used to start and stop the Genset automatically and manually with the help of the Auto/Manual switch on the board. The unit is provided with a variable to set the self on time as per the generator requirement.
The unit monitors the MAINS supply and automatically starts and stops the Genset. If the Genset fails to start in four attempts, the error light will start blinking.
The voltages are continuously monitored by the unit when the engine is running and the unit automatically shut down the engine if it finds the low voltage on the output of the Genset.
If a fault condition occurs, the FUEL solenoid will de-energize, the Choke relay will energize for 15 seconds and the Error light will start blinking. After removing the fault, press the Reset switch on the unit to get rid of the fault indication. The fault condition will also eliminate the presence of Mains Supply.
- Fail to start
- Under Voltage
If a fault condition occurs, the FUEL solenoid will be de-energized and the LED associated with this condition will turn on and the error LED will start blinking
If a fault condition occurs, the FUEL solenoid will be de-energized and the error light will start blinking. After removing the fault, press the RESET button (micro switch on the panel) on the front panel.
The panel is provided with a small jumper for Auto/Manual selection and a variable to adjust the self-time as per the Genset requirement. There is no need to put extra timer(s) for the following delays:
- Self on time
- Mains Sensing time
- Gen warm-up time
- Gen cool time
- Mains load time
Connection Diagram of EPH-106